|Home |||Register Login |||Wanted Manuals |||MarketPlace |||Members Area |||Manuals Manufacturer Directory |||UPC Lookup |||Information Pages |||Policy|
The Search Results for the Search Section to the left will appear here.
Installer : please leave these instructions with consumer . Consumer : please retain for Classic Series future reference . VENTED GAS FIREPLACE LOG SET AVAILABLE IN THE A . G . A . / C . G . A . CERTIFIED FOLLOWING LOG STYLES INSTALLATION AND Classic Oak OPERATING INSTRUCTIONS 18 " Model No . 6500742 . 6 ( Nat ) 18 " Model No . 4500741.6 ( LP ) 24 " Model No . 7400742.6 ( Nat ) 24 " Model No . 5500741.6 ( LP ) 30 " Model No . 9600742,6 ( Nat ) 30 " Model No . 6500741.6 ( LP ) Classic Designer Oak 18 " Model No . 6500742.7 ( Nat ) 18 " Model No . 4500741.7 ( LP ) 24 " Model No . 7400742,7 ( Nat ) 24 " Model No . 5500741.7 ( LP ) 30 " Model No . 9600742.7 ( Nat ) 30 " Model No . 6500741.7 ( LP ) Classic Split Oak 18 " Model No . 6500742.8 ( Nat ) 18 " Model No . 4500741.8 ( LP ) 24 " Model No . 7400742.8 ( Nat ) 24 " Model No . 5500741.8 ( LP ) 30 " Model No . 9600742.8 ( Nat ) 30 " Model No . 6500741.8 ( LP ) FOR NATURAL OR PROPANE GAS WARNING : Improper installation , adjust - IMPORTANT : READ THESE INSTRUCTIONS I ment , alteration , service or maintenance CAREFULLY BEFORE STARTING I can cause injury or property damage . Refer INSTALLATION OF YOUR LOG SET I to this manual . For assistance or additional Your Williams Log Set is to be installed only in a solid - fuel information consult qualified installer , ser - burning fireplace with a working flue constructed of noncom - vice agency or the gas supplier . bustible material . Solid fuels shall not be burned in a fireplace where a gas log set is installed . The minimum permanent vent opening provided by the fireplace chimney or chimney damp - FOR YOUR SAFETY I er to vent the flue products is listed on page 2 . The chimney Do not store or use gasoline or other flam - I damper must be fixed in a manner to maintain the minimum mable vapors and liquids in the vicinity of permanent vent opening . The installation , including provi - this or any other app ance . sions for combustion and ventilation air , must conform with the American National Standard National Fuel Gas Code FOR YOUR SAFETY Z223 . 1 and applicable local building codes . In Canada , the WHATTO DO IF YOU SMELL GAS installation must conform with the current CAN / CGA B149 . 1 1 . Do not try to light any appliance and B149 . 2 Installation Code . 2 . Do not touch any electrical switch ; do not use any phone in your building . 3 . Immediately call your gas supplier from a neighbor's phone and follow the gas supplier's instructions . 4 . If you cannot reach your gas supplier , call the fire department WILLIAMS FURNACE COMPANY 225 Acacia Street , Colton , CA 92324 USA ( 800 ) 266 - 0993 1 No . P923231
IMPORTANT : TO THE PURCHASER : Keep this warranty and the installation and home owner's instructions for your future reference . Limited Warranty The Manufacturer , Williams Furnace Co . , warrants this vented gas fireplace log set to the original purchaser under the following conditions : LIMITED ONE YEAR WARRANTY 1 . Any part thereof which proves to be defective in material or workmanship within one year from date of original purchase for use will be repaired or replaced at the Manufacturer's option , FOB its factory . 2 . No liability is assumed by the Manufacturer for removal or installation labor costs , nor for freight or delivery charges . LIMITATIONS 1 . THIS LIMITED WARRANTY IS THE ONLY WARRANTY MADE BY THE MANUFACTURER . IMPLIED WARRANTIES OF MERCHANTABILITY OR FITNESS FOR ANY PARTICULAR PURPOSE ARE LIMITED TO THE SAME ONE YEAR TERM AS THIS EXPRESS WARRANTY . UNDER NO CIRCUMSTANCES SHALL THE MANUFACTURER BE LIABLE FOR INCIDENTAL , CONSEQUENTIAL , SPECIAL OR CONTINGENT DAMAGES OR EXPENSES ARISING DIRECTLY OR INDIRECTLY FROM ANY DEFECT IN THE PRODUCT OR ANY COMPONENT OR FROM THE USE THEREOF . THE REMEDIES SET FORTH HEREIN ARE THE EXCLUSIVE REMEDIES AVAILABLE TO THE USER AND ARE IN LIEU OF ALL OTHER REMEDIES . Some states do not allow limitations on how long an implied warranty lasts , and some states do not allow the exclusion or limitation of incidental or consequential damages , so the above limitations or exclusions may not apply to you . 2 . This warranty does not include any charge for labor or installation . 3 . This warranty does not extend to painted surfaces nor to damage or defects resulting from accident , alteration , misuse or abuse , or improper installation . 4 . This warranty does not cover claims which do not involve defective workmanship or materials . DUTIES OF THE CONSUMER 1 . The vented gas fireplace log set must be installed by a qualified installer and operated in accordance with the installation and home owner's instructions furnished with the equipment . 2 . Any travel , diagnostic costs , service labor , and labor to repair the defective unit will be the responsibility of the owner . 3 . A bill of sale , cancelled check , payment record or permit should be kept to verify purchase date to establish the warranty period . 4 . Have the installer enter the requested information in the space below . GENERAL 1 . The Manufacturer neither assumes nor authorizes any parson to assume for it any other obligation or liability in connection with said equipment . / 2 . Service under this warranty should be obtained by contacting your dealer . Provide the dealer with the model number , serial number and purchase date verification . 3 . If , within a reasonable time after contacting your dealer , satisfactory service has not been received , contact : Customer Service Department , 225 Acacia Street , Colton , California 92324 U . S . A . , for assistance . 4 . THIS WARRANTY GIVES YOU SPECIFIC LEGAL RIGHTS , AND YOU MAY ALSO HAVE OTHER RIGHTS WHICH VARY FROM STATE TO STATE . INSTALLATION INFORMATION MODELNO . SERIALNO . ORIGINAL PURCHASER ADDRESS CITYAND STATE DEALER ADDRESS ClTYAND STATE INSTALLATION DATE SIGNED BY ( Dealer or authorized representative who certifies that this appliance has been installed in accordance with Manufac - turer's instructions and local codes ) .
WILLIAMS CLASSIC SERIES GAS LOG SETS IMPORTANT INFORMATION Do not use this log set if any part has been under be removed . This will insure long life and trouble - water . Immediately call a qualified service technician free operation . An annual inspection and cleaning to inspect the appliance and to replace any part of of the vent system by a qualified agency is recom - mended . the control system and any gas control which has been under water . The minimum inlet gas supply pressure for the pur - The gas log set must be isolated from the gas sup - pose of input adjustment is 5 " for Natural Gas and ply piping system by closing its individual shut - off 1 1 " for Propane Gas . The maximum inlet gas supply valve during any pressure testing of the gas supply pressure for this burner is 14 " for Natural and Pro - system at test pressures equal to or less than 1 / 2 pane Gas . psig . The gas log set and its individual shut - off valve must be disconnected from the gas supply piping A fireplace screen must be in place when the log set system when testing at pressures in excess of 1 / 2 is burning . Unless other provisions for combustion psig . air are provided , the screen shall have an opening ( s ) for introduction of combustion air . When a glass fire - Keep the area of the gas log set clear and free from place enclosure ( door ) is used , operate the gas log combustible materials , gasoline and other flammable set with the glass doors open . vapors and liquids . The minimum size fireplace in which the log set is certified to be installed , is listed in theTechnical Data MAINTENANCE : Periodically remove the logs and examine the burner assembly . If dirty , clean with a Table below . To center the log set in the fireplace , an stiff brush . Also examine the area around burner air additional 2 " to 3 " in rear width is recommended . shutter , and pilot . Any dirt or lint in this area should Classic Series Technical Data Table Minimum Fire Box Dimensions BTU Rating Front Opening Rear Width * Depth Height Nat . Propane 18 " 27 " 17 " 13 " 18 " 65,0O0 45,000 24 " 33 " 22 " 14 " 18 " 74,000 55,000 30 " 39 " 26 " 14 " 18 " 96,000 65,000 * An additional 2 " to 3 " is recommended to center the log set . Minimum Free Opening Area of Chimney Damper for Venting For Factory Built Fireplaces For Masonry Built Fireplaces Log Set Sizes Log Set Sizes Chimney 18 " 24 " 30 " 18 " 24 " 30 " Height 15 ' 30 SQ " 35 SQ " 49 SQ " 41 SQ " 46 SQ " 58 SQ " 20 ' 25 SQ " 29 SQ " 41 SQ " 38 SQ " 42 SQ " 52 SQ " 21 SQ " 25 SQ " 35 SQ " 25 ' 30 ' 19 SQ " 22 SQ " 31 SQ " 34 SQ " 38 SQ " 47 SQ "
PARTS LIST FOR CLASSIC SERIES GAS LOG SETS NOTE : Log styles and part sizes will vary depending upon the log set ordered . When ordering replacement pads , be sure to indicate your log set model ( The parts for the Classic Oak 24 " Set are illustrated below ) , GLOWING 7 16 , / 9 8 14 Safety Control System ( Item No . 14 ) . . . . . . . . . . . _ . - _ . . . . . . . . . . _ . . . . . . . . . . ' _ l . . , . . . . . . . . . . . r . LOCATOR . . . . . . 27 TAB , , , / " HEATSTHAIEBLD . . . . . . . . . . . . . . . . . . , . . . 30 _ _ L 23 . . . _ , 28 _ q _ - - 22 - - - - TOGASSUPPLY 37 _ " / - _ _ L _ lll / _ " _ Item15 . Replacement pads may be obtained from your L ' / _ t _ _ 3 / . _ 2 , ' 33 - nearest Williams Dealer . For assistance in 23 . . , , 1 " . k , . . _ - ( _ - locating a Dealer , you may contact the factory 20 " TOBURNER at the address listed on the front page .
HOW TO INSTALL YOUR WILLIAMS CLASSIC GAS LOG SET The Williams Classic Gas Log Set must be installed by a qualified technician . Instructions must be followed carefully to insure proper performance and full benefit from your gas log set . Williams Classic Gas Logs must be installed only in EMBER PLACEMENT a wood burning fireplace with the minimum venting Sprinkle embers ( Item 11 ) lightly and evenly over requirements met ( see Pg . 3 ) . Check parts list to be entire surface of the granules or vermiculite . Replace sure all parts are included . Gas supply pipe must be the grate so that bottom tabs on the Iog - locator I / 2 " or larger . Use 3 / 4 " if the gas line is longer than 20 ' . brackets fit over the back edge of the pan locking it in position . REFER TO PARTS LIST ( PAGE 4 , 5 ) WHEN FOLLOWING THESE INSTRUCTIONS . INSTALLATION OF LOG SET ( be sure gas to the fireplace is off ) 1 . Remove grate ( Item 7 ) from carton and attach log Iocators ( Item 10 ) to the two outer bars of the grate with bolts and nuts . Log Iocators should be posi - tioned at the middle of the bars with the two taller pins facing the front . Example of burner flame pattern 2 . Connect nipple ( item 38 ) to regulator inlet . Attach the smaller elbow from connector kit ( item 15 ) to the LOG PLACEMENT opposite end of the nipple and tighten . Proper log placement is important to insure proper 3 . Place the burner assembly ( item 8 ) into the fire - performance of your Williams Classic Gas Log Set . place so the open burner pan faces to the room . Be sure to follow log placement instructions careful - ly . Optional log placement patterns , are explained on 4 . Place the grate ( item 7 ) over the burner pan ( item page 7 . 8 ) so the log Iocator brackets ( item 10 ) fit over the back edge of the burner pan to lock it in position . PLACEMENT OF BOTTOM LOGS Place the front and rear bottom logs on the grate ( Fig . 5 . Center this assembly in the fireplace and place as 1 ) . The longest log is placed in front . The log Iocators far back in the fireplace as possible . Remove grate insure that adequate space between the logs are ( item 7 ) for gas connection and granule placement . maintained for a cleaner burn . 6 . Connect larger elbow from connector kit ( item 15 ) to gas supply . Using connector kit tubing , connect gas supply to the small connector elbow on the regulator ( installed in step 2 ) . 7 . Turn on the gas to the fireplace and test for leaks with soapy water solution . ( Never use open flame for testing ) . GRANULE OR VERMICULITE PLACEMENT Figure 1 With the burner off and grate removed , fill the burner pan completely with granules or vermiculite ( Item 12 ) . Slope the granules or vermiculite at the same angle as burner pan . Note : Use vermiculite only when your log set is fueled by propane gas . Do not use granules with a propane gas log set . 6
FOR YOUR READ BEFORE LIGHTING WARNING : If you do not follow these instructions exactly , a fire or explosion may result causing property damage , personal injury or loss of life . The Williams Classic Gas Log Set has a pilot which â€¢ If you cannot reach your gas supplier , call the fire must be lit by hand . When lighting the pilot , follow department . these instructions exactly . 2 . Use only your hand to push in or turn the gas 1 . BEFORE LIGHTING , smell all around the gas control knob . Never use tools . If the knob will not log set area for gas . Be sure to smell next to the floor push in or turn by hand , don't try to repair it . Call a because some gas is heavier than air and will settle qualified service technician . Force or attempted re - on the floor . pair may result in fire or explosion . WHAT TO DO IF YOU SMELL GAS 3 . Do not use the gas log set if any part has been â€¢ Do not try to light the appliance under water . Immediately call a qualified service technician to inspect the gas log set and to replace â€¢ Do not touch any electrical switch , do not use any phone in your building . any part of the control system and any gas control which has been under water . â€¢ Immediately call your gas supplier from a neighbor's phone . Follow the gas supplier's instructions . LIGHTING INSTRUCTIONS 1 . STOP ! Read the safety information above . 3 . Wait five ( 5 ) minutes to clear out any gas . If you then smell gas , STOP ! Follow " 1 " in the safety 2 . Push in gas control knob slightly and turn clock - information above . If you don't smell gas , go to the wise _ to " OFF " ( Fig . 14 ) . NOTE : The knob next step . cannot be turned from " PILOT " to " OFF " unless the 4 . Find Pilot - follow metal knob is pushed in slightly . Do not force . tube from gas control . The pilot is above the burner tube behind the front log . 5 . Turn knob on gas control counterclockwise to " PILOT " . Figure 15 6 . Push in control knob all the way and hold in . Immediately light the pilot with a match . Continue to hold the control knob in for approximately one ( 1 ) minute after the pilot is lit . Release knob and it will 1 . LIGHTING - turn knob to " OFF " , . , " _ and wait 5 pop back out . Pilot should remain lit . If it goes out , minutes before lighting . repeat step 3 through 6 . OFF PILOT ON * If knob does not pop out when released , stop and immediately call your service technician or gas sup - plier . * If the pilot will not stay lit after several tries , turn the gas control knob to " OFF " and call your service technician or gas supplier . 1 . Use " OFF " 2 . Turn Dialto " PILOT " 3 , Turn knob to " ON " 7 . Turn gas control knob counterclockwise onlywhencomplete position . With _ to light burner . to " ON " to light your set . shutdown is neces - match ready press knob in and hold for 60 sec - sary . 8 . Periodically check the pilot flame ( Fig . 15 ) for onds while lighting pilot . proper flame pattern . Figure 14 TO TURN OFF THE GAS LOG SET 1 . From the " On " position , turn control knob clockwise _ to the " PILOT " position . The log set will extinguish and the pilot will remain lit . 2 . If complete shutdown is desired , from the " PILOT " position , push in the control knob slightly and turn clockwise _ to the " OFF " position . Do not force the knob .
PLACEMENT OF MIDDLE AND TOP LOGS Option 1 : Place the two middle logs on the bottom logs . The knotholes of the middle logs are placed over the front pins of the log Iocators , with the opposite ends crossed , resting on the back bottom log ( Fig , 2 ) . Top logs are placed with one end resting on the knothole of the middle logs and one end resting on the top of the front bottom log ( Fig . 3 ) . Figure 4 Option 3 : Reverse the log Iocator on one side so that the longer pin is toward the back of the log set ( Fig . 5 ) . Place the middle logs so they are parallel , resting on the bottom logs with the knotholes cover - ing the pins . Place the top logs parallel to each other across the middle logs ( Fig 6 ) . Figure 2 Figure 5 Figure 3 Option 2 : Place the middle logs as instructed under option 1 ( Fig . 2 ) . One top log is then set with one end on a middle log knothole and the other end resting on the bottom front log . The other top log is set with one end on the knothole of the other middle log and the other end resting on the bottom rear log ( Fig 4 ) . Figure 6 OPTIONAL LOG PLACEMENT PATTERNS SUMMARY The below three illustrations show the three log placement patterns available for Williams Classic Gas Log Sets . The mirror image of each of the illustrations is also approved . Option 1 Option 2 Option 3
PILOT BURNER ADJUSTMENT The pilot burner is preset at the factory and should adjustment screw ( located under the cap screw ) normally not require any adjustment . However , should slowly clockwise to reduce the flame , or counter - adjustment be necessary , the following steps should clockwise to increase the flame . The adjustment be taken : screw can be turned so that the pilot flame is com - With the pilot burner lit and the control knob in the pletely extinguished . The pilot flame should be a pilot position , remove phillips head screw ( item 29 ) quiet soft blue flame with yellow tipping which encir - and heat shield face ( item 26 ) . Carefully remove the cles the thermocouple tip . cap screw located on the control valve ( see Figure 10 ) . Using a long narrow screwdriver , turn the pilot Reassemble the cap screw and gasket to the valve body , insuring that the cap screw and gasket are firmly seated on the valve body . Replace heat shield 7 face ( item 26 ) and phillips head screw ( item 29 ) . Turn Example the control knob to the " on " position to assure proper of burner PILOT _ ignition of the log set . pilot flame ADJUSTMEN " CAP SCREW Figure 10 DAMPER STOP CLAMP INSTRUCTIONS The Damper Stop Clamp with hex bolt ( Fig . 11 ) is _ rovided as a means to prevent full closure of the damper blade . The clamp is easily attached to most damper blades with pliers or wrench , and must be permanently instaLled . The clamp is designed to prevent accidental closure of the damper when in - stalled as illustrated ( Figs . 12 and 13 ) . Should the @ clamp not fit , or fail to provide the permanent vent opening listed in the table found on page 2 , have a ) ermanent stop installed , remove the damper blade Figure 13 Figure 11 Figure 12 or have the damper cut to provide the minimum ) ermanent opening required .